Telecom Power Supply
When city power or main power shot off, to keep the telecom teminal device work well, diesel generator should play as a standby power,which can provide the emergency power to the telecom load.
Diesel generator can assure there is no stop working of telecome device.
Diesel generator can work 24 hours each day and there is no stop, output keep at rated power, 1hours overload per 12hours is allowed.
Altitude：below 1000 meters.
Ambient temperature: Lowest :-15°C, highest:+ 45°C
Depend on user different requirement,standby power can equipped with super silent generator. Noise below 75dBA @ 7 meters.
3.Diesel generator self protection and self start/stop function:
In following condition, diesel generator can stop automatically and protect itself。Low oil pressure, high water temperature, overspeed, overload and fault phase.
Diesel generator with AMF which can start automatically. Diesel generator with ATS which can start and transfer automatically.
If city power or main power shut off, diesel generator can start automatically within stipulated time ,for instance, 20second, and provide power to the load. If city power come back , diesel generator will stop automatically, ATS will make load power supplied by city power or main power.
No Stop Telecome power supply：
Diesel generator with ATS and Deepsea DSE7320 controller can provide no stop power to the terminal load. Self start and Self stop desigh can make the device station run without guard.
Diesel generator should be able to keep the coolant temperature at 15～50℃；oil temperature keep at 15～30℃。
Diesel generator should start successfully,the probabiltiy should be over 90%. after get the remote start order. If the generator fail to start three times, the standby generator should be started.
Diesel generator should stop automatically after get the remote stop order. There is two stop way, one is normal stop, the other is emergency stop.